Whether you require Tips and Advice about radiators, plate heat exchangers or heating systems in general AEL have the technical expertise to provide guidance on your system design and which products are best suited to your application.
Should you not find the answer to your problem in our “Tips and Advice” articles and require any help feel free to contact our technical sales office.
Delivery Terms & Conditions
- AEL will contact you during the next working day to discuss a convenient delivery date of your order.
- Orders delivered by road transport are delivered to the nearest convenient hard standing position and the consignee is responsible for offloading.
- Standard delivery is between 9am and 5pm on weekdays only, prices for timed deliveries and weekend deliveries can be provided by our sales office upon request.
- Please note that missed deliveries can be rescheduled and are chargeable.
- We're open 9am to 5pm weekdays with Saturday collections possible by prior arrangement.
- Please note that Cast Iron Radiators are heavy so we advise that you double check the weight of your order and the maximum weight your vehicle can carry as AEL can accept no responsibility for the suitability of your vehicle.
Guide To Water Flow Rates and Pressure
Below provides a guide to water flow rates and pressure when sizing a plate heat exchanger.
Low Pressure Installations A gravity or low Pressure Installation in a standard two storey house with a cold feed water tank in a loft serving a hot water cylinder on the first floor.
The bathroom taps would have approximately 0.2bar pressure.
A shower head would have approximately 0.1bar pressure.
Taps on the ground floor would have approximately 0.4 - 0.5bar pressure.
A kitchen sink cold water tap would be supplied from the incoming mains water supply and would be high pressure at anything above 1bar pressure.
Approximate Guide to Flow Rates for Taps and Showers
Standard basic bath tap ¾" = 0.25 l/s
Standard basic basin taps ½" = 0.166 l/s
Standard basic bath mixer ¾" tap = 1.2 l/s
Monobloc basin mixer with 10-12mm connections = 0.066 l/s to 0.083 l/s
Standard basic ½" kitchen tap = 1.2 l/s
Monobloc sink mixer = 0.13 l/s
A gravity shower on the ground floor with 0.5bar pressure could provide approximately 0.16 l/s to 0.2 l/s so best check with manufacturer.
Mains Fed Systems
Mains fed systems normally operate at 2.5 to 3bar pressure and give good flow rates in excess of .25 l/s to .416 l/s but this can depend on the size of the mains water supply pipe coming into the property..
Water Pressure and Water Flow Good pressure does not mean you will get good flow and good flow does not mean you will have good pressure. A standard dripping tap can have good pressure but very poor flow rate where as for example a stream can have very good flow rate but very low pressure.
Static and Dynamic Pressures Static pressure is the pressure when all the taps are turned off and no water flow is occurring. Dynamic pressure is when taps are turned on and the pressure becomes increasingly lower as more taps are opened. As more and more water flows through the system more and more resistance has to be overcome because every pipe length, valve and fitting creates more and more "frictional" resistance to the flow. Lower resistance means less dynamic pressure reduction and greater flow and greater resistance means less flow.
Gravity showers will only be just adequate so if you want a good shower on a gravity system it will need to be pumped at a pressure of 1bar or above for a single headed shower but if you are using body jets as well then you would need a 2.4 to 3 bar pump. When using a pump in a shower system you must consider the size of your existing hot and cold water tanks.
An average shower time is approximately 8 to 12 minutes.
A twelve minute shower with a flow rate of 0.25 l/s and would use 180 litres of water.
With a split of 60% of hot to 40% of cold water a shower could use about 108 litres of hot water. An average domestic hot water cylinder in a 3 bedroomed house would have an approximate capacity of 117 litres so your 12 minute shower will have used approximately 92% of your hot water capacity.